Air Conditioning Service
Servicing all major Central & Ductless Mini-Split Brands
What is involved in air conditioner service?
- Wash outside coil or condensing coil. This is found inside the casing of the central unit, most commonly seen as the main unit of central air conditioners. The mini-split unit has a small casing unit that is shorter and rectangular in shape.
- Clean indoor evaporator coil. The evaporator coil works with the indoor unit, found in both central and mini-split air conditioners to cool and condition indoor air that flows over it by extracting heat and moisture.
- Check and clean drains that flow from the exterior unit to the interior unit and back and in central air conditioning units drain out of the system properly to a drain pipe found near the unit. Keeping condensate drains cleaned prevents harmful contaminants like mold, mildew, and other bacteria from growing in the pipe.
- Check operation and electrical components to ensure that your cooling system is efficiently operating and will continue to work throughout the year.
- Check refrigeration and temperature readings to calibrate your cooling system to ensure that when it's hot outside your system keeps you cool inside.
ckSmithSuperior's 16 Point Tune-Up for your Heating System
10. Check the CAD cells and relay for proper operation. On units with stack relays, clean the helix of soot and reinstall. Disconnect the motor circuit and test the relay for safety.
11. Steam systems: The boiler should be drained, flushed, and refilled to 3/4 full on the gauge glass. Gauge glass should be cleaned if dirty or replaced if needed. The low water cutoff should be flushed and tested. Remove the pressure control from the boiler and thoroughly clean out sediment that may have collected.
12. Hot water systems: Check the altitude gauge for pressure on the system, and also to make certain there is water at the highest radiator. IF there is an expansion tank, it should be drained. Examine air pressure thanks for waterlogging. Check the aquastat reading so that settings for hot water have a 30 degree differential between the circulator and the high limit. (Example: if the high limit is set for 200 degrees for boiler water, the reverse acting aquastat should be set no lower than 170 degrees for the circulator to cut in.
13. For warm air system: Check the heat exchanger for any visible cracks or holes. Check air filters and replace or clean them, depending on the type of filter. Check humidifier for proper operation. Replace media in accordance with the manufacturer's instructions. Check blower belts and adjust for proper tension.
14. Examine the position and setting of draft control.
15. Perform a complete combustion analysis and efficiency test procedure using a digital combustion analyzer.
16. We will leave the work area as tidy as we found it and provide a verbal report of the work performed, including any additional work that may be necessary for your heating system to run at peak performance.